Uni-/Bidirectional gateway between EnOcean wireless devices and the KNX bus. Over 100 device profiles (EEP EnOcean Equipment Profiles) allow easy and secure connection of various EnOcean sensors and actuators to KNX installations.
The unit KNX ENO 630 serves as a unidirectional gateway between EnOcean radio devices and the KNX/EIB bus. With this device, commands and measured values of EnOcean wireless sensors can be transferred to the KNX bus, for example, to control KNX actuators.
For EnOcean sensors the device is based on the so-called EnOcean Equipment Profiles (EEP). The implemented profiles mostly are specified in the data sheets of the sensors. For the control of EnOcean actuators corresponding EEPs are emulated.
Come primo gateway KNX sul mercato, il nuovo KNX ENO 626 secure supporta la comunicazione radio criptata con i dispositivi EnOcean. La messa in funzione è semplice come al solito: la crittografia può essere attivata individualmente per tutti gli 8 canali. Successivamente, i sensori e gli attuatori EnOcean che supportano la sicurezza possono essere appresi come prima. L'utente ottiene una maggiore sicurezza senza perdere il comfort.
The KNX ENO 630 is organized in 16 channels. Each channel can be assigned to one of the following functions.
Link from EnOcean sensor to KNX:
- Switching and contact functions
- Shutter up/down
- Window contacts
- Window handles
- Key cards switches
- Ressure switches
- Temperature sensors
- Humidity sensors
- Light sensors
- Presence sensors
- Gas sensors
- Room control devices
- Automated counter devices
- Environmental sensors (weather station)
- Digital inputs
Control / logic:
The configuration of the device and the channels is done using the ETS software via the KNX bus. For the teach-in of the wireless components the keys and the display in the device are used.
- Tracking circuit
- Lighting control
- Logical functions
- Gates (e.g. AND, OR, XOR)
Mounting and connection
The mounting can be done on a wall surface (e.g. brick-work or wood). The mounting holes match for a 55 mm flush-mounted box. The power supply of the device is realized via the bus.
The repeater function is used for extend distances between sensors and actuators. The KNX ENO 630 is a so-called level-1 radio repeater.
Bus monitor function
The integrated bus monitor function is used for system diagnostics directly on the device. The device can display both EnOcean telegram as well as KNX telegrams.
Configuration: KNX ENO Tool
The KNX ENO Tool software can be used to configure the Links between various EnOcean-Sensors and the KNX/EIB EnOcean-Gateway KNX ENO 626/630/632/6347636. The device configuration of the Gateway can be read, modified, exported and saved back to either the same or another Gateway. EnOcean Bus Monitor showing the EnOcean Telegrams send over the KNX Bus.
- 16/24/32 channels for sensors, actuators or logic
- Integrated logic and control functions
- Support for more than 100 profiles (EEP)
- Integrated graphical display
- Connections: KNX, internal antenna
- Wall-mount housing, white
- Dimensions (WxLxH): 81 x 81 x 25 mm
KNX ENO 626 secure and KNX ENO 636 secure are recommended for new installations.